Zone Valves Play an Important Role in your Hot Water Heating System
By Mark J. Donovan
||Is your hot water heating system continuously running or not working at all? When you turn down the thermostat does hot water continue to flow through your hot water heating system? If so, it is possible that you have a failed hydronic zone valve.
A hydronic zone valve is used in hot water heating systems. In conjunction with your home’s thermostat, circulating pump and boiler, the hydronic zone valve helps control the flow of hot water through your hot water heating system.
Zone valves are fairly simple devices and as a result are frequently used in hot water heating systems. Typically multiple zone valves are used in a home heating system.
This allows multiple thermostats to be placed at different levels in the home or in different rooms of the house, so that you can independently control the heat to each level or room.
|Zone valves are low voltage controlled via your thermostat. They are powered by a local 24V AC power supply source usually located near the boiler. When the thermostat turns on, the zone valve allows hot water to flow through the hot water heating system.
Unfortunately hydronic zone valves have the tendency to fail, and when they do fail, they frequently fail to the open position. When this happens the zone valve allows hot water to continuously flow through the hot water heating system, regardless of the thermostat setting. This causes the floor or room to heat up and the boiler to constantly run. When this happens you should turn the boiler off and call a plumbing or heating contractor.
In the event a hydronic zone valve fails closed, no hot water will flow through the system regardless of the thermostat setting. To mitigate this zone valve fail condition, plumbing/heating contractors frequently install multiple zone valves and circulator pumps into the hot water heating system. This solution helps to protect the house from freezing winter temperatures. If one of the hydronic zone valves fails, the other heating zones will still be operational and prevent the threat of frozen pipes. Again, if the zone valve fails closed, you should immediately call a plumber or heating contractor.
Repairing a hydronic zone valve can be quite straight forward. Many models are designed so that the valve does not need to be replaced. Instead the electric motor assembly, or powerhead, that makes up the upper portion of the hydronic zone valve can be swapped out with a replacement subassembly.
For information on installing a shower pan membrane liner for a ceramic tile shower, see the Shower Pan Membrane Liner Installation eBook from HomeAdditionPlus.com. The Shower Pan Membrane Liner EBook will quickly teach you the step-by-step process for installing the shower pan membrane liner correctly. It includes instructions on framing the shower stall, pouring the pre-slope and shower base mortar, and installing the shower pan membrane liner.
For information on how to tile a custom ceramic tile shower, see the “How to Tile a Custom Ceramic Tile Shower eBook” from HomeAdditionPlus.com. This eBook will quickly provide you with step-by-step instructions on how to measure and install ceramic tile in a shower, including the installation of tile on shower walls, floors and curbs. It provides detailed instructions for every step in the process of tiling a custom ceramic tile shower and is loaded with instructional pictures!
- How Hydronic Zone Valves Work Video
- Hot Water Expansion Tank Video
- How Hot Water Circulator Pumps Work Video
Additional Plumbing Resources from Amazon.com
Get Free Bathroom Remodeling Price Quotes with No Obligation!
Fill out our 3-5 minute quick and easy form, and receive a free price quote on a bathroom remodeling project from one of our pre-screened and licensed bathroom remodeling contractors. This process is free and there is no obligation to continue once you receive your bathroom addition price estimate.